SECTION 1. Section 144 of Chapter 164 of the General Laws, as appearing in the 2016 Official Edition, is hereby amended by striking out subsection (c) and inserting in place thereof the following subsection:-
(c)(1) Upon the undertaking of a significant project on a public way exposing confirmed natural gas infrastructure, and with sufficient notice, a municipality or the commonwealth shall submit written notification of the project to a gas company. The gas company shall survey the project area for the presence of Grade 1 or Grade 2 leaks and set repair and replacement schedules for all known or newly detected Grade 1 or Grade 2 leaks. The gas company shall ensure that any shut off valve in the significant project area has a gate box installed upon it or a reasonable alternative that would otherwise ensure continued public safety and that any critical valve that has not been inspected and tested within the past 12 months is verified to be operational and accessible. The gas company shall provide the repair and replacement schedule of gas leaks to the municipality or the commonwealth.
(2) Upon the undertaking of any planned project involving excavation for purposes of performing maintenance on or construction involving any gas mains or services by gas company employees, or any blasting work, the gas company shall ensure that its employees first locate and identify and mark all gas gates and valves, and verify that all are cleared, operational and accessible in clear sight at ground level in advance of any excavation; and that said gas gates and valves are left cleared, and operational following any such project.
(3) The gas company shall ensure that any shut off valve in the significant project area has a gate box installed upon it by its employees to ensure continued public safety.
(4) The gas company shall provide the municipality or the commonwealth with written confirmation that the gas gates and valves have been cleared, inspected and tested by its employees and found to be capable of accepting a gate key; and, shall provide the municipality or commonwealth with undated, correct information if the location of gates or valves is determined to have been previously improperly located.
(5) Failure to undertake verification that gas gates and valves have been cleared, and are both operational and accessible prior to the start of and following an excavation, or blasting work, shall be subject to a fine of up to $10,000. Failure to submit written confirmation of such verification shall be subject to a fine of $200 per day.
The information contained in this website is for general information purposes only. The General Court provides this information as a public service and while we endeavor to keep the data accurate and current to the best of our ability, we make no representations or warranties of any kind, express or implied, about the completeness, accuracy, reliability, suitability or availability with respect to the website or the information contained on the website for any purpose. Any reliance you place on such information is therefore strictly at your own risk.